SpecSeal Series 44+ EZ Path Single Split Retrofit Plate
Mfr. Part #: EZP144RS
Roll Over To Zoom
The EZ Path Retrofit Device is designed to restore the ratings for overfilled cable sleeve penetrations. The device features a built-in fire and smoke sealing system that can attach either to the sleeve or the barrier surface.The EZ Path Retrofit Device consists of a heavy g...View More Details
About This Product
The EZ Path Retrofit Device is designed to restore the ratings for overfilled cable sleeve penetrations. The device features a built-in fire and smoke sealing system that can attach either to the sleeve or the barrier surface.
The EZ Path Retrofit Device consists of a heavy gauge galvanized steel housing containing intumescent materials that expand rapidly when exposed to fire or high temperatures to close off the void area. Its unique two-piece design quickly installs around cable bundles and extended sleeves and can even accommodate standard conduit bushings. The square device shape allows cable exit or entry from multiple directions.
- Easy to install
- No additional firestopping required
- Sized for 2 in (2.197 in [56 mm] to 2.375 in [60 mm] OD) and 4 in (4.500 in [114 mm]) trade size EMT or rigid steel conduit sleeves or stubs
- 50% to 100% cable fill
- Works with extended or flush sleeves
- Bring overfilled sleeves back into code compliance
- Cable Tray
EZ Path Retrofit Device restores non-compliant overfilled sleeve conditions in walls and floors. Cable capacity ranges from 50 to 100% visual fill. The two piece split device facilitates installation around existing cable bundles. The steel backplate attaches directly to the end of the steel sleeve. For flush-mounted sleeves, mounting tabs allow for attachment to the substrate.
All new data comm cable penetrations shall be routed through factory supplied, maintenance-free, fire-rated pathway devices (Ex. EZ Path Fire Rated Pathways). For existing sleeves where cable fill percentage exceeds listed system specifications, a factory-supplied, fire-rated retrofit device shall be installed. The device shall be a two-piece split design with intumescent materials and allow 50 to 100 percent visual fill. The device shall be UL Certified and tested to ASTM E814 (UL1479) and CAN/ULC-S115.
- ASTM E814 (UL1479)
- Division 7, 07 84 13, Penetration Firestopping
- Division 26, 26 00 00, Electrical
- Division 27, 27 00 00, Communications